For fixed installation indoors, outdoors, in the ground, in water and in concrete.
To be used as energy and control cable for fixed installation in moist and dry rooms, outside, underground and in water. To be used for power stations, switching stations and local exchange networks, where mechanical damage is not expected. For using NYY-cables DIN VDE 0298 part 1 is valid as VDE 0276-603 and as HD 603 p. 1-3 G, HD 603 page 1 is valid for current-carrying capacity together with use 0276 part 1000. The product corresponds to the directive 2014/35/EU (low voltage directive).
Structure & Specifications
|Conductor material||copper, bare|
|Conductor class||class 1, from 25 sqmm class 2|
|Insulation||PVC DIV 4|
|Sheathing material||PVC DMV5|
|Colour outer sheath||black|
|Flame-retardant||VDE 0482-332-1-2/IEC 60332-1-2|
|For outdoor use||yes|
|Maximum permitted conductor temperature, °C||70 °C|
|Permitted outer cable temperature, fixed, °C||70 °C|
|Permitted outer cable temperature, in motion/during installation, °C||-5 - +70 °C|
|Nominal voltage Uo||600 V|
|Nominal voltage U||1000 V|
|Colour of outer sheath||black|